Table of Contents
Types Of Valve Used In Industries and Plumbing
There are a large variety of valves and valve configurations to suit all services and conditions; different uses (on/off, control), different fluids (liquid, gas etc; combustible, toxic, corrosive etc) different materials and different pressure and temperature conditions. Valves are for starting or stopping flow, regulating or throttling flow, preventing back flow or relieving and regulating pressure in fluid or gaseous handling applications.
Common valve types include:
Ball,Butterfly,Check, Diaphragm, Gate, Globe, Knife Gate, Parallel Slide, Pinch, Piston, Plug, Sluice, etc.
The following types of valves are used in a variety of applications, these descriptions may provide a basic guideline in the selection of valves.
Because of their excellent operating characteristics, ball valves are used for the broadest spectrum of isolation applications and are available in a wide range of sizes and materials and are available in full fl ow and full through conduit.
Advantages – quick acting, straight through fl ow in either direction, low pressure drop, bubble tight shut off & operating torque, easily actuated.
Disadvantages – temperature limitiations on seating material, long “relative” face to face dimension.
The butterfly valve derives its name from the wing-like action of the disc which operates at right angles to the fl ow. It’s main advantage is a seating surface which is not critical. It is designed for fl ow isolation. The disc impinges against a resilient liner to provide bubble tightness with low operating torque. Compact and with a simple construction, butterfly valves facilitate easy pipe arrangement. Due to disc, they have slightly reduced fl ow characteristics.
Advantages – quick acting, good regulating characteristics, compact & light, low pressure isolation. Butterfly valves are simple, reliable and range in size from 40mm to 1000mm and beyond. They can be controlled by a notched lever, handwheel as well as by pneumatic or electric actuator. A shaft turns a disc 90º within a pipe. The disc angle within the pipe can provide a restriction varying from drip-tight through to almost full fl ow (except very small sizes).
Sometimes referred to as a non-return valve, the check valve prevents back-flow in the piping by constantly keeping fluid flowing in one direction. Check valves operate automatically. Some piston/disc check valves are spring loaded for fast operation, (minimum cracking pressure should be specified). Vertical downwards flow requires a spring loaded check valve.
Swing Check Valves: – Swing & Wafer checks cease reverse flow with a flap that swings onto a seat. Use swing checks only for forward flow that is horizontal or vertical upward.
Piston Check Valves: – Piston & Spring checks cease reverse flow with a spring loaded plunger.
Ball Check Valves:– Ball checks have a ball that slides into a hole as forward flow slows. Consider a ball check for semi-solids such as pulp or effluent.
Titlting Disc Check Valves: – Tilting Disc check valves are similar to Swing check valves but in most installations, slamming is minimised upon reversal of fl ow so noise and vibration are reduced.
Globe/Stop Valves: – The flow path through globe valves follows a changing course, thereby causing increased resistance to flow and considerable pressure drop. Because of the seating arrangements, globe valves are the most suitable for throttling flow, however avoid extremely close throttling when the repeatable pressure drop exceeds 20%. Close throttling creates excess noise, vibration and possible damage to valves and piping. The valve is named after is globular body. Compared to gate valves, globe valves are designed to open and close more quickly. Their flow characteristics can be changed by re-configuring their discs.
Advantages – best shut off (not drip tight above 50NB) & regulating.
Disadvantages – high pressure drop (head loss), unidirectional.
Stop Check Valves (SDNR): – Stop check valves are essentially the same as Globe valves, except there is no mechanical connection between the stem and the disc. They provide a combination Stop valve and a Piston check valve in one valve. However, they are not designed for throttling. They are used in steam boiler outlet piping when two or more boilers are connected to a common header. Valves must be installed with pressure under the disc, and when the stem is raised, only boiler pressure can raise the disc whenever boiler pressure exceeds header pressure. They prevent backflow from the header to boiler.
Wedge Gate Valves: – Commonly used in industrial piping for stop or isolating – to turn on and shut off the flow as opposed to regulating flow. Gate valves are named from the gate-like disc which operates at a right angle to the path of the flow. Gate valves are general service valves that can be made in a broad spectrum of sizes using a variety of different materials. Wedge gate valves are metal seated but are also available with resilient seat insert if drip tight shut off is required. They can meet the demands of a wide range of pressure and temperature conditions and is available in full port.
Advantages – low pressure drop, straight through flow either direction.
Disadvantages – slow acting, bulky. Not drip tight shut off (over 150NB). Do not partially open as this will cause damage to seat/disc.
Knife Gate Valves: – Useful for many applications in larger sized pipework (50mm up). Unlike traditional gate valves, they are able to throttle (at lower pressures) depending on line media and degree of opening. Metal seated knife gate valves are not leak tight shut off. Some knife gate valves have a resilient seat in order to ensure they close drip-tight. Available in v-port, o-port and lined they are ideally suited for the control of effluent, slurries, waste products, semi solids, pulp, bulk powders. Most knife gate valves are designed for single flow direction.
Parallel Slide Gate Valves: – Popular in steam applications as the energised disc design handles thermal expansion without sticking like wedge gate valves. Another advantage is lower torque then wedge gate valves especially in venturi (Ferranti) reduced bore configuration. Parallel slide valves consist of two parallel gates that are energised against the seat at all times by springs or a wedging spreader bar between the two gates. No mechanical stress is exerted between the discs, and the valve is not subjected to dangerous strains in opening and closing. This design of valve maintains fluid tightness without the aid of wedging action. These valves are used for saturated and super heated steam.
Pipeline Slab Gate Valves: – Available in parallel solid slab and expanding 2 piece wedging slab. Both styles protect the seat area from the flow in all operating positions. These valves have a full through conduit configuration with a hole in the slab. Slab style gate valves have seats that are spring energised. The expanding slab features two opposed sliding v-shape segments that maintain pressure against the seats. These valves are for API6D pipeline applications but are also used for API6A wellhead valves. All these valves are made in metal to metal and soft seat configuration.
Plug valves are valves with cylindrical or conically-tapered “plugs” which can be rotated inside the valve body to control flow through the valve. The plugs in plug valves have one or more hollow passageways going sideways through the plug, so that fluid can flow through the plug when the valve is open. Plug valves are simple and often economical.
Pressure Reducing Valves
Water pressure reducing valves are installed to reduce the water pressure to the desired or accepted limits. They normally have a spring and diaphragm that is adjusted to certain limits depending on the pressure of the water being served. They can be installed in copper, PVC and other different pipe types. They could normally last more than 10 years when maintained properly.
Angle valves are typically installed at the water intake of plumbing fixtures or appliances. Angle valves could fail when high pressure is detected on the line. They are used to shut off water
Needle Valve The use of needle valves touches a variety of industries. These products are used to regulate the flow of gases and liquids and allow a precision resistance to flow, keeping fragile gauges safe from surges of a pressurized non-viscous substance such as water, oil or gases.
Tilting disk check valves use a pivoted disk as the closure element. They are similar to swing check valves but the pivot axis is close to the center of the flow stream. The disk remains closed against the seat under no- flow conditions and is forced open by the flow. Tilting disk check valves are best used in applications which require rapid response and when freedom from sticking is essential.
Mechanical engineering is one of the most physically demanding professions that involve designing, manufacturing, and maintaining mechanical systems. A mechanical engineer's work involves utilizing...
Management is an essential component of every project and team. A competent manager is indispensable in guiding the team, owning outcomes, and mediating conflicts. Engineering managers, in...