Fusible plug Diagram, Working | Boiler Mounting and Accessories
BOILER MOUNTINGS AND ACCESSORIES
Boiler mountings are the devices mounted on the boiler surface for safe operation, efficient working, control steam generation and easy maintenance of the boiler.
In accordance with the Indian boiler regulation the following mountings should be fitted to the boilers.
- Two safety valves- Click here for more info.
- Two water level indicators – Click here for more information
- A pressure gauge
- A steam stop valve
- A feed check valve
- A blow-off cock
- An attachment for inspector’s test gauge
- A man hole
- Mud holes or sight holes
Read more : Introduction to Boilers | Classification Of Boilers
Function of Fusible Plug :
To protect the boiler against damage due to overheating for low water level.
It is fitted on the fire box crown plate or over the combustion chamber at its approprirate place.
A common form of fusible plug is illustrated in Fig. It consists of a hollow gun metal body screwed into the fire box crown: The body has a hexagonal flange to tighten it into the shell. A gun metal plug having a hexagonal flange is screwed into the gun metal body. There is another hollow gun metal plug separated from the metal plug by an annulus of fusible metal. The fusible metal is protected from fire by flange on the hollow gun metal plug.
Under normal condition when the water-level in the boiler shell is normal, the fusible plug is fully submerged under water. In this case, the heat from the fusible plug is being conducted to water which keeps the fusible metal at an almost constant temperature and below its melting point. But when the water level falls below the fusible plug, it gets uncovered from water and is exposed to steam. The heat conduction from the fusible plug to steam is very little compared with that to water. Hence fusible plug becomes overheated and it melts with the result that the hollow gun metal plug falls down making a hole. The steam and water being under pressure immediately rush to fire box and extinguish the fire.
The fusible plugs should generally be renewed after a period of about two years as they are liable to become defective over a long period of use (because they are subjected to heat on one side and scale deposits on the other).
Mechanical engineering is one of the most physically demanding professions that involve designing, manufacturing, and maintaining mechanical systems. A mechanical engineer's work involves utilizing...
Management is an essential component of every project and team. A competent manager is indispensable in guiding the team, owning outcomes, and mediating conflicts. Engineering managers, in...
One thought on “Fusible plug Diagram, Working | Boiler Mounting and Accessories”
What is the minimum diameter of the small end of the tapered hold of the fire side fusible plug.