Table of Contents
Refrigerators Compressors – Types Of Compressor used in HVAC
Introduction To Refrigerator Compressors :
A typical refrigeration system consists of several basic components such as compressors, condensers, expansion devices, evaporators, in addition to several accessories such as controls, filters, driers, oil separators etc. For efficient operation of the refrigeration system, it is essential that there be a proper matching between various components. Before analyzing the balanced performance of the complete system, it is essential to study the design and performance characteristics of individual components. Except in special applications, the refrigeration system components are standard components manufactured by industries specializing in individual components. Generally for large systems, depending upon the design specifications, components are selected from the manufacturers’ catalogs and are assembled at site. Even though most of the components are standard off-the-shelf items, sometimes components such as evaporator may be made to order. Small capacity refrigeration systems such as refrigerators, room and package air conditioners, water coolers are available as complete systems. In this case the manufacturer himself designs or selects the system components, assembles them at the factory, tests them for performance and then sells the complete system as a unit.
Refrigerator Compressors :
A compressor is the most important and often the costliest component (typically 30 to 40 percent of total cost) of any vapour compression refrigeration system (VCRS). The function of a compressor in a VCRS is to continuously draw the refrigerant vapour from the evaporator, so that a low pressure and low temperature can be maintained in the evaporator at which the refrigerant can boil extracting heat from the refrigerated space. The compressor then has to raise the pressure of the refrigerant to a level at which it can condense by rejecting heat to the cooling medium in the condenser.
Types Of Compressors used in Refrigerator and HVAC
Classification of compressors
Compressors used in refrigeration systems can be classified in several ways:
a) Based on the working principle:
i. Positive displacement type
ii. Roto-dynamic type
In positive displacement type compressors, compression is achieved by trapping a refrigerant vapour into an enclosed space and then reducing its volume. Since a fixed amount of refrigerant is trapped each time, its pressure rises as its volume is reduced. When the pressure rises to a level that is slightly higher than the condensing pressure, then it is expelled from the enclosed space and a fresh charge of low-pressure refrigerant is drawn in and the cycle continues. Since the flow of refrigerant to the compressor is not steady, the positive displacement type compressor is a pulsating flow device. However, since the operating speeds are normally very high the flow appears to be almost steady on macroscopic time scale. Since the flow is pulsating on a microscopic time scale, positive displacement type compressors are prone to high wear, vibration and noise level.
Depending upon the construction, positive displacement type compressors used in refrigeration and air conditioning can be classified into:
i. Reciprocating type
ii. Rotary type with sliding vanes (rolling piston type or multiple vane type)
iii. Rotary screw type (single screw or twin-screw type)
iv. Orbital compressors, and
v. Acoustic compressors
In roto-dynamic compressors, the pressure rise of refrigerant is achieved by imparting kinetic energy to a steadily flowing stream of refrigerant by a rotating mechanical element and then converting into pressure as the refrigerant flows through a diverging passage. Unlike positive displacement type, the roto-dynamic type compressors are steady flow devices, hence are subjected to less wear and vibration.
Depending upon the construction, roto-dynamic type compressors can be classified into:
i. Radial flow type, or
ii. Axial flow type
Centrifugal compressors (also known as turbo-compressors) are radial flow type, roto-dynamic compressors. These compressors are widely used in large capacity refrigeration and air conditioning systems. Axial flow compressors are normally used in gas liquefaction applications.
b) Based on arrangement of compressor motor or external drive:
i. Open type
ii. Hermetic (or sealed) type
iii. Semi-hermetic (or semi-sealed) type
In open type compressors the rotating shaft of the compressor extends through a seal in the crankcase for an external drive. The external drive may be an electrical motor or an engine (e.g. diesel engine). The compressor may be belt driven or gear driven. Open type compressors are normally used in medium to large capacity refrigeration system for all refrigerants and for ammonia (due to its incompatibility with hermetic motor materials). Open type compressors are characterized by high efficiency, flexibility, better compressor cooling and serviceability. However, since the shaft has to extend through the seal, refrigerant leakage from the system cannot be eliminated completely. Hence refrigeration systems using open type compressors require a refrigerant reservoir to take care of the refrigerant leakage for some time, and then regular maintenance for charging the system with refrigerant, changing of seals, gaskets etc.
In hermetic compressors, the motor and the compressor are enclosed in the same housing to prevent refrigerant leakage. The housing has welded connections for refrigerant inlet and outlet and for power input socket. As a result of this, there is virtually no possibility of refrigerant leakage from the compressor. All motors reject a part of the power supplied to it due to eddy currents and friction, that is, inefficiencies. Similarly the compressor also gets heated-up due to friction and also due to temperature rise of the vapor during compression. In Open type, both the compressor and the motor normally reject heat to the surrounding air for efficient operation. In hermetic compressors heat cannot be rejected to the surrounding air since both are enclosed in a shell. Hence, the cold suction gas is made to flow over the motor and the compressor before entering the compressor. This keeps the motor cool. The motor winding is in direct contact with the refrigerant hence only those refrigerants, which have high dielectric strength, can be used in hermetic compressors. The cooling rate depends upon the flow rate of the refrigerant, its temperature and the thermal properties of the refrigerant. If flow rate is not sufficient and/or if the temperature is not low enough the insulation on the winding of the motor can burn out and short-circuiting may occur. Hence, hermetically sealed compressors give satisfactory and safe performance over a very narrow range of design temperature and should not be used for off-design conditions.
The COP of the hermetic compressor based systems is lower than that of the open compressor based systems since a part of the refrigeration effect is lost in cooling the motor and the compressor. However, hermetic compressors are almost universally used in small systems such as domestic refrigerators, water coolers, air conditioners etc, where efficiency is not as important as customer convenience (due to absence of continuous maintenance). In addition to this, the use of hermetic compressors is ideal in systems, which use capillary tubes as expansion devices and are critically charged systems. Hermetic compressors are normally not serviceable. They are not very flexible as it is difficult to vary their speed to control the cooling capacity.
In some (usually larger) hermetic units, the cylinder head is usually removable so that the valves and the piston can be serviced. This type of unit is called a semi-hermetic (or semi-sealed) compressor.
Hammers are some of the most essential tools in any toolbox. They come in different types and sizes, each designed for specific purposes. If you’re doing any kind of construction work, DIY...
Bridges are a crucial part of our infrastructure, allowing us to connect and traverse various terrains. They play a significant role in transportation, enabling the movement of people and goods...